BS Non automatic fire-fighting systems in buildings. Code of practice. BS gives recommendations for non-automatic. BS – Regulations on Dry Riser Design, Installation, Testing and Maintenance. Dry Risers in the UK must be designed and installed in accordance with BS BS outlines recommendations for non-automatic fire-fighting systems in buildings. Supersedes BS First published Second (present edition), January Came into effect 31 January This full revision updates.
New code of practice for non automatic fire-fighting systems in buildings published called British Standard BS In January a new code of . BS Non automatic fire-fighting systems in buildings. Code of practice. standard by BSI Group, 01/31/ View all product details. Most Recent. BS - fire-fighting systems. AIM OF TASK. Inspection of and, where practicable, a wet test of private under-ground fire hydrants should be.
BS This is a full revision of the standard. The principal changes are to update the recommendations for: • flow tests and pressures; • rising and falling. As metallic services they should be main equipotentially bonded at the point of entry to the building back to the main earthing terminal (along. BS Non automatic fire-fighting systems in buildings. Code of practice ( British Standard. UK Dry Risers are nationwide providers of dry and wetrisers, with dry riser design , manufacture and testing available at a competitive price. Service.